Last week I shared a blog post by Allison Bailes that discussed patent trolls, infrared cameras, and home inspectors. Today, I’d like to share why I care about this topic.
My infrared camera is definitely the coolest home inspection
toy tool that I own. I can bust my dog for sitting on the couch, prove to my kids that they’re not really “freezing”, and confirm that my wife is hot. In addition to that stuff, I’ve discovered lots of useful ways to use this camera for home inspections.
When we first started offering infrared inspections, we had one camera that we juggled between everyone. Today, I’m proud to say that all of the inspectors at Structure Tech have infrared cameras. We don’t always use infrared cameras during home inspections, and we charge extra for a full infrared inspection, but these cameras frequently come in handy for identifying and documenting defects. The most obvious use of an infrared camera is to identify insulation defects in walls or air leaks in attics, but the images below show several other examples of ways that infrared cameras can be useful to home inspectors.
We use infrared cameras to help identify leaking tiled showers. As I mentioned in my blog post about shower leaks, we test tiled showers by flooding the shower base with about 2″ of water, and then letting the water sit in the shower for about 45 minutes to an hour. If the tiled shower base leaks, water will show up on the ceiling below.
Through the diligent use of an infrared camera, we can almost always identify these leaks before they stain the ceiling below. The images below show a few examples of tiled shower leaks identified with infrared cameras during home inspections. Of course, we always verify these leaks with a moisture meter before reporting them as leaks. Cold spots in ceilings aren’t always leaks.
I recently shared this photo in my blog post about not connecting downspouts directly to yard drains, but here it is again. The blue area is wet.
It’s one thing to say there’s moisture intrusion in a basement, but having an infrared image that shows the area that’s wet really helps to tell the story.
Scanning electric panels with an infrared camera can easily identify overheated conductors or circuit breakers. The panel shown below had an overheated neutral wire, which I suspect was the result of a loose connection; there were two neutrals connected to a single lug.
For the record, only one neutral wire is allowed at each lug.
Inspecting In-Floor Heat
Inspecting in-floor heat with an IR camera quickly shows which areas are heated. The image below shows a heated garage floor.
Quickly Inspecting Radiators
It’s much easier to make sure a radiator is heating properly by just pointing an infrared camera at it. The radiator shown below wasn’t heating properly.
Suspected Exterior Leaks
We rarely use infrared cameras outdoors because the sun really messes with our results, but we’ll occasionally get a nice image at the exterior that illustrates suspected water intrusion. The image below shows a suspected leak at the wall of a stucco home with missing kickout flashing.
Again, we don’t report leaks without verifying them with a moisture meter. The only way of confirming a leak at a stucco home is to perform invasive moisture testing, which is a service we don’t offer. We leave that up to the folks that specialize in that service. Infrared inspections are not an acceptable substitute for invasive moisture testing on stucco homes.
We may have never found this hidden floor register without the use of an IR camera. This was a new construction home where the carpet installers apparently went a little too fast.
We have several more examples of things that can be identified with an infrared camera at our web page on infrared inspections, but they’re mostly focused on energy loss.
Author: Reuben Saltzman, Structure Tech Home Inspections