Everyone knows that oxygen is required for a fire, right? So where does the oxygen come from for your furnace, gas water heater, fireplace, and other fuel-burning appliances? Typically, this is supplied through a combustion air duct. You’ll find combustion air ducts on almost all newer houses, and on many houses that have had new furnaces or water heaters installed. While it was once thought that these ducts were not as necessary on older, drafty homes, newer research has shown that these leaks are not always reliable, and they are never desirable.
In homes that have bathroom exhaust fans and kitchen exhaust fans, it is especially important to have a combustion air duct installed. While combustion air ducts are not intended to provide make-up air for exhaust fans, this is really what they end up doing, in addition to replacing the air that gets used by the fuel-burning appliances. While it’s beyond the scope of this blog to get in to the specifics of how these are all inter-related, there are a couple of simple, but very important things to do as a homeowner.
- Don’t block the duct opening. This is the easiest, most obvious thing that you can do (or not do?). The photo below shows a typical combustion air duct, with the opening un-obstructed. You’ll feel cold air coming out of this duct on to the floor in the winter, and this is air that needs to come in to the house. I’ve seen people tape the bottoms of these ducts shut, and I’ve seen rags stuffed in to the duct. This is very bad idea, as carbon monoxide could be produced from lack of combustion air. To help keep cold air from dumping in to the house, a loop can be created at the bottom of the duct, or a bucket placed below it, as long as it doesn’t reduce the overall opening.
- Make sure the intake is un-obstructed. In Minnesota, the intake is required to be located at least 12” above the ground, to help keep it clear from snow, leaves, and other debris. If the intake is closer than this, consider having it raised. If there is a damper installed at the opening at the exterior, remove it. Dampers allow air out, not in! I’ve seen dampers installed on many homes when the vinyl siding installers didn’t know what the opening was for, so they installed a damper, which blocks the combustion air opening.
- Keep the intake clean. This is something you should check at least once a year. The intake will be located at the exterior of your home, and looks like the one pictured below. There should be a 1/4 steel screen installed, which will keep larger pests from entering in to your home. If this screen is dirty, clean it with a wet/dry vac.
When I inspect houses, I check for all these things and I share this information with my clients.